This plug type is for Canada, Columbia, El Salvador, Japan, Mexico, Nicaragua, Panama, South Korea, Taiwan, United States, and Venezuela. a
|Power Type||60A three-phase Delta power|
|Nameplate Rating b c||
|Expected Utility Power Sources (Provided by Site)||
With either of these two utility power sources, each of the 4-pin power plugs connects to all three lines and also to safety ground. With this power source, the power plug does not have a neutral connection.
|Power Plug and Number of Cords (Supplied with Product)||IEC 60309 CEE17, pin and sleeve, 60A, Blue (3Ø250V), 3P4W, with 9-hour keying, IP67 watertight plug
(Walther Electric brand is shown below. Actual brand supplied may vary.)
Two AC feeder box cords per cabinet, top or bottom egress.
The minimum bend radius limit for the power cord is 16.5 cm (6.5in.). Do not bend the power cord tighter than this limit.
|AC Feeder Box Power Cord Connections to Site Power (For Redundancy)||The power cord on the left AC feeder box in the cabinet connects to one site power source. The power cord on the right AC feeder box in the cabinet connects to the second site power source.|
|Power Receptacle or Connector and Circuit Breakers (Provided by Site)||IEC 60309 CEE17, pin and sleeve, 60A, Blue (3Ø250V), 3P4W, with 9-hour keying, IP67 watertight receptacle or connector
Example receptacles (similar products are available from other companies):
Example connectors for use with cordage (similar products are available from other companies):
Example connector for use with 1-inch NPT fitting for connection to conduit: d
Example connector for use with 1 ¼-inch NPT fitting for connection to conduit: d
Site to supply two receptacles or connectors per cabinet. e
One three-pole site circuit breaker required for each power cord; site must provide required site circuit breakers.
Each AC feeder box on separate power source connection.
a Bahrain, Brazil, Lebanon, Philippines, and Saudi Arabia require discussions with the site team to determine the appropriate power feature for the specific site.
b Do not use this table to determine power consumption, to estimate current draw, or to estimate heat generation. For these parameters, see Environmental Elements. Nameplate ratings are a statement of product certification.
c Frequency rating is 50 or 60 Hz for all products.
d Conduit adapters do not connect to the ground terminal of the connector. Consult your local code grounding requirements before using adapters.
e Obtain connectors from any source. Connectors are available from Teradata by ordering kit 2021-K902. One kit is required per cabinet.