This plug type is for Europe, Australia, Africa, Asia, Middle East, Territories of the United Kingdom, Russia, Belarus, Territories of France, Territories of Denmark, Territories of the Netherlands, and the Pacific (excluding Taiwan, Japan, South Korea) that use IEC 30A/32A three-phase Wye, 220V to 240V line-to-neutral. Also used for specialized, energy saving data center sites in North America that use 220V to 240V line-to-neutral. Not suitable for a 120V Wye power source that is traditional in North America.
30A/32A three-phase Wye, 230V L-N power:
|Nameplate Rating a b||
|Expected Utility Power Source (Provided by Site)||
Three-phase Wye with a line-to-neutral voltage of 200V to 240V
(Not suitable for a Wye source with a line-to-neutral voltage of 120V that is traditional in North America.)
|Power Plug and Number of Cords (Supplied with Product)||
IEC 60309 CEE17, pin and sleeve, 30A/32A, Red (400V), 4P5W, with 6-hour keying, IP44 splash-proof plug
(Walther Electric brand is shown. Actual brand supplied may vary.)
Two AC feeder box cords per cabinet, top or bottom egress.
The minimum bend radius limit for the power cord is 15.1 cm (5.9 in.). Do not bend the power cord tighter than this limit.
|AC Feeder Box Power Cord Connections to Site Power (For Redundancy)||The power cord on the left AC feeder box in the cabinet connects to one site power source. The power cord on the right AC feeder box in the cabinet connects to the second site power source.|
|Power Receptacle or Connector and Circuit Breakers (Provided by Site)||IEC 60309 CEE17, pin and sleeve, 30A/32A, Red (400V), 4P5W, with 6-hour keying, IP44 splash-proof receptacle or connector
Example receptacle (similar products are available from other companies):
Example connectors for use with cordage (similar products are available from other companies):
Example connector for use with ¾-inch NPT fitting for connection to conduit: c
Site to supply two receptacles or connectors per cabinet. d
One three-pole site circuit breaker required for each power cord; site must provide required site circuit breakers.
Each AC feeder box on separate power source connection.
a Do not use this table to determine power consumption, to estimate current draw, or to estimate heat generation. For these parameters, see Environmental Elements. Nameplate ratings are a statement of product certification.
b Frequency rating is 50 or 60 Hz for all products.
c Conduit adapters do not connect to the ground terminal of the connector. Consult your local code grounding requirements before using adapters.
d Obtain connectors from any source. Connectors are available from Teradata by ordering kit 2021-K903. One kit is required per cabinet.