This plug type is for Canada, Columbia, El Salvador, Japan, Mexico, Nicaragua, Panama, South Korea, Taiwan, United States, and Venezuela.a
30A/32A phase-phase or single-phase power:
|Nameplate Rating b c||
|Expected Utility Power Sources (Provided by Site)||
With either of these two utility power sources, each of the 4-pin power plugs connects to all three lines and also to safety ground. With this power source, the power plug does not have a neutral connection.
|Power Plug and Number of Cords (Supplied with Product)||
IEC 60309 CEE17, pin and sleeve, 30A, Blue (3Ø250V), 3P4W, with 9-hour keying, IP67 watertight plug
(Walther Electric brand is shown. Actual brand supplied may vary.)
Four AC feeder box cords per cabinet, top or bottom egress.
The minimum bend radius limit for the power cord is 10.9 cm (4.3 in.). Do not bend the power cord tighter than this limit.
|AC Feeder Box Power Cord Connections to Site Power (For Redundancy)||The cabinet contains two AC feeder boxes on the left side of the cabinet and two AC feeder boxes on the right side of the cabinet. Each AC feeder box has one power cord (four total). The two power cords on the left side of the cabinet connect to one site power source. The two power cords on the right side of the cabinet connect to the second site power source.|
|Power Receptacle or Connector and Circuit Breakers (Provided by Site)||IEC 60309 CEE17, pin and sleeve, 30A, Blue (3Ø250V), 3P4W, with 9-hour keying, IP67 watertight connector or receptacle
Example receptacles (similar products are available from other companies):
Example connectors for use with cordage (similar products are available from other companies):
Example connectors for use with ¾-inch NPT fitting for connection to conduit: d
Example connector for use with 1-inch NPT fitting for connection to conduit:d
Site to supply four receptacles or connectors per cabinet. e
One three-pole site circuit breaker required for each power cord; site must provide required site circuit breakers.
a Bahrain, Brazil, Lebanon, Philippines, and Saudi Arabia require discussions with the site team to determine the appropriate power feature for the specific site.
b Do not use this table to determine power consumption, to estimate current draw, or to estimate heat generation. For these parameters, see Environmental Elements. Nameplate ratings are a statement of product certification.
c Frequency rating is 50 or 60 Hz for all products.
d Conduit adapters do not connect to the ground terminal of the connector. Consult your local code grounding requirements before using adapters.
e Obtain connectors from any source. Connectors are available from Teradata by ordering kit 2021-K904. Two kits are required per cabinet.